The RIKEN RI (radioactive isotope) Beam Factory is scheduled to commence operations in 2006, and its maximum energy will be 400 MeV u(-1) for ions lighter than Ar and 350 MeV u(-1) for uranium. The beam intensity will be 1 pmicroA (6 x 10(12) particles s(-1)) for any element at the goal. For the hands-on-maintenance and the rational shield thickness of the building, the beam loss must be controlled with several kinds of monitors. Three types of radiation monitors will be installed. The first one consists of a neutron dose equivalent monitor and an ionisation chamber, which are commercially available area monitors. The second one is a conventional hand-held dose equivalent monitor wherein the logarithmic signal is read by a programmable logic controller based on the radiation safety interlock system (HIS). The third one is a simple plastic scintillator called a beam loss monitor. All the monitors have threshold levels for alarm and beam stop, and HIS reads all these signals.